This page provides one detailed case study and several short summaries of case studies for dry swales.
Project Summary – International Plaza Drive Improvements
Location: City of St. Ann, Missouri
Owners: City of St. Ann, Missouri
Designer: HR Green
Year of Completion: 2012
Design Features: Dry swale, rocked inlets and check dams
Total Drainage Area: 6-acres
Total Construction Cost: $770,500
HR Green worked with the City of St. Ann, Missouri to design a point of entry into the City. The pavement at this location was in disrepair. Evident ponding of stormwater occurred at the location and was one of the reasons for the pavement failure. This project is generally located south of Interstate 70, between Cypress Road and Ashby Road within the city limits of St. Ann, Missouri. International Plaza Drive is a designated collector roadway , running in the east-west direction, serving as a means to move traffic from local streets to nearby arterial roads.
Improvements for this project include the complete reconstruction of the roadway with new Portland cement concrete (PCC) pavement and integral curb, striped bike lanes, and a meandering concrete sidewalk/pathway. To address the requirements of the regulatory agencies with oversight, namely the Metropolitan St. Louis Sewer District (MSD), the City utilized engineered structures to address the water quality needs of the project. This approach minimized maintenance costs and maintenance activities associated with the use of a dry swale.
The project was designed in 2011 and constructed in 2012.
This project road design inverted the proposed roadway section and directed all of the roadway’s stormwater runoff into the center median. The existing curb inlets and appurtenances were no longer needed and were removed. The new drainage pattern results in stormwater runoff to four dry swales that receive flow from a total of 6.01 acres, with approximately forty to fifty percent of that total area being impervious surface. The project extent is 2.20-acres
Design general performance criteria for stormwater management for this project was based on Metropolitan St. Louis Sewer District (MSD) Section 4.080. Stormwater management was required because the redevelopment area exceeded 1 acre of disturbed area.
The dry swale drainage areas outside of the pavement section include an area inlet to serve as an overflow structure to accept flow from the typical 15-year, 20-min design storm. Earthen check dams or ditch checks were installed within the dry swale areas such that the maximum water elevation in these areas will be three (3) inches below the adjacent top of curb; any flow in excess of this volume will flow over the ditch checks and into the downstream area inlet. Depths of flow (15-year, 20-min) above the earthen check dams were calculated in order to verify that stormwater would not overtop the adjacent top of curb and onto the roadway. Berm placement is approximately every 200 to 400 feet along the dry swale and is constructed with a 1:1 slope and a two-foot width at the top. Soils at the site were Hydrologic Soil Group C and D.
The design intent was to follow all applicable rules and regulations, but circumstances within the design process required deviations from the guidelines, as noted below:
While these dry swales areas were sized to hold flows generated from a 1.14-in rainfall event, inevitably more intense storms will fall within the region. In these situations, the proposed area inlets installed at the downstream ends of the dry swale areas will capture excess stormwater and will be routed downstream to the existing system, consisting of intakes and pipes.
Some design complications were realized on this project as compliance with hydraulic grade line (HGL) requirements was difficult to attain in all areas of the storm sewer design. As a minimum, MSD notes that “…the [HGL] at any inlet or storm manhole shall not be higher than two (2) feet below the inlet sill or top of manhole.” However, due to the assumed HGL starting point within the Hydraflow model (pipe enters two reaches downstream of the connection point to the existing system), there are instances in the design where this requirement was unable to be attained. Through trial and error, the pipe sizes and flowlines of the proposed storm sewer system were tweaked in an attempt to correct this problem to no avail. Since the differential flow for the project is essentially non-existent, it is assumed that the existing system currently operates under this condition as well.
The cost to complete the roadway, bike and pedestrian sidewalks and associated items, signals, lighting, signing and striping, and landscaping and streetscaping was $770,428.
Summary of costs for dry swale case study - International Plaza Drive Improvements.
Link to this table
|Description||Unit||Quantity||Unit cost (dollars)||Extension (dollars)|
|Furnish/Place Type 1 ditch liner||Cubic yard||3.2||80||257.78|
|Ketucky Bluegrass sodding||Cubic yard||1226.3||6||7.357.87|
|Bermuda or Zoysia sodding||Square yard||1963.6||7||13,744.87|
|3/8 inch gravel||Cubicyard||268.5||40||10,738.73|
|3/4 inch gravel||Cubic yard||268.5||40||10,783.73|
|Bioretention soil media||Cubic yard||1073.9||50||53,693.67|
|MSD Type 4 geotextile||Square yard||1000.7||11||11007.88|
|Shrubs (#5 container or 1-gallon container)||Each||30||90||2.700|
|Trees (2.5-inch caliper or 1-gallon container)||Each||3||325||975.00|
The ongoing maintenance of the dry swale was taken on by the City of St. Ann (link here for information on operation and maintenance of dry swales). Maintenance of the dry swale included the following.
An Annual BMP Maintenance Report is submitted to MSD by the City of St. Ann before March 31st. A MSD inspector periodically inspects the BMP.
Below are summaries of additional case studies for dry swales..
A project incorporating bioswales into a local park located east of downtown Houston, Texas. The document describing the project provides a summary of the project, including design, expected pollutant removal, LEED features. Includes detail drawings; soil mixes used; information on underdrains, curbs, and inlets; plant materials; landscaping; maintenance; cost information; photos and schematics. Source: Houston Land Water Sustainability Forum.
This PowerPoint presentation, Low Impact Development in the Transportation Environment: Lessons Learned in North Carolina (Winston, 2014), summarizes several case studies utilizing swales. The focus is on different design options and features and their effect on swale performance. Includes some design information, performance results, and numerous photos, schematics, and other images.
Three bioswales were constructed at the Lane Transit District (LTD) Springfield Station, Springfield, Oregon. Two swales function as major elements and one as a minor element. This case study provides a minimum of information on design but provides a summary of monitoring conducted at the site. Link.
Biofilters For Stormwater Discharge Pollution Removal - Excerpt from this document: "This document is an attempt to compile the best available information on the design and use of biofilters (bioswales, vegetated filter strips, and constructed wetlands) so that those sites that may have an application of one or the other of these vegetated filtering systems will have information to make the best decision on the design, construction, implementation, and maintenance of these Best Management Practices. It is not a design manual but a practical, based on experience and knowledge of sites that implemented these BMPs, useful information on what works and does not work when designing, constructing, and operating them."
"A bioswale was installed as part of the Nevin Welcome Center building project in 2010. The project, which includes a green roof, and several other sustainable features, received LEED Gold from the U.S. Building Council. The bioswale was designed to slow and clean storm water runoff from the parking lot while providing an attractive garden landscape, which is more ecologically-minded than a traditional storm drain system. The garden is used as a teaching landscape to showcase the benefits and functions of a bioswale garden."
The study report for this project focuses on sustainable features of this project.